Shipment & Storage
Position discs at 10% open so that they are unseated.
The faces of each valve should be covered to prevent damage to the seat face, disc edge, or valve interior.
Store indoors, preferably with ambient temperatures between 5°C and 30°C.
Open and close the valves every 3 months.
Ship and store valves so that no heavy loads are applied to the bodies.
Butterfly valves should be installed if possible a minimum of 6 pipe diameters from other line elements, i.e. elbows, pumps, valves, etc. Sometimes this is not feasible, but it is important to achieve as much distance as possible.
Where the Butterfly valve is connected to a check valve or pump, keep enough space between them to ensure the disc does not interfere with the adjacent equipment.
As a rule of thumb, Butterfly valves be installed with the stem in the vertical position with the actuator mounted vertically directly above it, however, there are some applications where the stem should be horizontal. The .pdf file below tells you why the stem somtimes must be positioned horizontally.
Related Industry Knowledge
- Butterfly valve history
- Butterfly valve structure features
- Butterfly valve advantages
- Ball valve
- Ball valve history
- Ball valve advantages
- Ball valve classification
- Three-way ball valve features
- Regulating valve
- Regulator valve classification
- Avoiding problems with Butterfly va...
- Introduction to valves - Globe valves
- Body designs of Globe valves
- Disk & Seat & Stem of Globe valves
- Physical properties of stainless steel
- Construction of a Globe valve
- Flow direction of Globe valves
- Advantages and disadvantages of Glo...
- Typical Applications of Globe valves
- Introduction to Valves - Gate valves