Pressure Independent Control Valves (PICV) can help reduce energy costs and increase occupant comfort in heating and cooling coil applications in buildings. A PICV is best described as two valves in one: a standard 2-way control valve and a balancing valve. PICV obtain optimal results because only the necessary amount of hot water (in GPM) and chilled water (in GPM) is delivered to the heating and cooling coils. Standard 2-way control valves allow for overflow and underflow especially if the CV is oversized or undersized. This generates excess water to the pump to compensate for their inaccuracy, which increases pumping cost. The actuators on PICV valves do not cycle as often as standard 2-way valves to compensate for pressure changes in the system that impact the flow, which results in energy savings. Here is a simplified explanation of PICV operation using a two-valve system. The second valve (V2 in the graphic below) regulates the pressure differential across the first valve (V1) using a rolling diaphragm element counter-acted by a spring. The first valve is a calibrated variable orifice device adjusted by the actuator (similar to a standard modulating control valve).
The diaphragm reacts to the system and regulates the pressure differential across the actuated control valve orifice to maintain its flow rate.On a PICV (see graphic below), when pre-setting the maximum flow rate, the inlet orifice changes in size, which does not interfere with the length of the stroke. When modulating, the orifice areas are affected by the actuator using the full stroke. This results in the orifice area changing in size with a vertical movement.
Related Industry Knowledge
- Butterfly valve history
- Butterfly valve structure features
- Butterfly valve advantages
- Ball valve
- Ball valve history
- Ball valve advantages
- Ball valve classification
- Three-way ball valve features
- Regulating valve
- Regulator valve classification
- What is a Control Valve?
- Why Control Valves used?
- Control valve Principles of Operation
- Control Valve Arrangement
- Why a Steam Control Valve is used i...
- What is the principle of operation ...
- Requirements for the use of regulat...
- What general terms are the pneumati...
- Application of pneumatic regulating...
- What are the industrial application...